Installed on a DIN rack in the switchboard.
Housing made of a flame-retardant polymer. The TELEMANDO device is equipped with a rechargeable battery (the unit can work during a power outage) and a two-position reset type switch. When the ON button is pressed, the device outputs a 12 V signal to the emergency luminaire to simulate the emergency mode. The OFF position simulates the service mode, i.e. disabling the luminaires in the emergency mode when the power is off during maintenance or service. 12 V voltage is output to the luminaires, switching the luminaires from the emergency mode to the standby mode.
Maximum 35 luminaires in a block. Maximum wiring length 250 m. Wire cross-section area: 0.75 mm² minimum, 1 to 1.5 mm² recommended. Maximum power consumption 0.5 W. Minimum battery charge time 24 hours.
- Educational institutions
- HoReCa / hotels / restaurants / cafes
- Medical institutions
- Office and administrative premises
- Stairs / hallways
- Stores / boutiques
- Transport hubs (railway stations, airports)
- Clm App4
- 0 to +40